text:
Smoke detector
From Wikipedia, the free encyclopedia
Jump to: navigation, search
Smoke Detector COFEM with approved EN 54-7
A smoke detector is a device that senses smoke, typically as an indicator of fire. Commercial security devices issue a signal to a fire alarm control panel as part of a fire alarm system, while household smoke detectors, also known as smoke alarms, generally issue a local audible or visual alarm from the detector itself.
Smoke detectors are housed in plastic enclosures, typically shaped like a disk about 150 millimetres (6 in) in diameter and 25 millimetres (1 in) thick, but shape and size vary. Smoke can be detected either optically (photoelectric) or by physical process (ionization); detectors may use either, or both, methods. Sensitive alarms can be used to detect, and thus deter, smoking in areas where it is banned. Smoke detectors in large commercial, industrial, and residential buildings are usually powered by a central fire alarm system, which is powered by the building power with a battery backup. Domestic smoke detectors range from individual battery-powered units, to several interlinked mains-powered units with battery backup; with these interlinked units, if any unit detects smoke, all trigger even if household power has gone out.
The risk of dying in a home fire is cut in half in homes with working smoke alarms. The US National Fire Protection Association reports 0.53 deaths per 100 fires in homes with working smoke alarms compared to 1.18 deaths in homes without (2009-2013). Some homes do not have any smoke alarms, some do not have working batteries; sometimes the alarm fails to detect the fire.[1]
Contents
[hide]
1 History
2 Design
2.1 Ionization
2.2 Photoelectric
2.3 Carbon monoxide and carbon dioxide detection
2.4 Performance differences
3 Commercial
3.1 Conventional
3.2 Addressable
4 Residential
4.1 Batteries
4.2 Reliability
4.3 Installation and placement
5 Standards
5.1 EN54 European standards
5.1.1 Coverage of smoke and temperature detectors with European standard EN54
5.2 Australia and United States
6 Legislation
7 References
8 External links
History[edit]
The first automatic electric fire alarm was patented in 1890 by Francis Robbins Upton,[2] an associate of Thomas Edison.[3] George Andrew Darby patented the first European electrical heat detector in 1902 in Birmingham, England.[4] In the late 1930s Swiss physicist Walter Jaeger tried to invent a sensor for poison gas.[5] He expected that gas entering the sensor would bind to ionized air molecules and thereby alter an electric current in a circuit in the instrument.[5] His device did not meet its purpose: small concentrations of gas had no effect on the sensor's conductivity.[5] Frustrated, Jaeger lit a cigarette and was soon surprised to notice that a meter on the instrument had registered a drop in current.[6] Smoke particles from his cigarette had apparently done what poison gas could not.[6] Jaeger's experiment was one of the advances that paved the way for the modern smoke detector.[6] In 1939 Swiss physicist Ernst Meili devised an ionization chamber device capable of detecting combustible gases in mines.[7] He also invented a cold cathode tube that could amplify the small signal generated by the detection mechanism to a strength sufficient to activate an alarm.[7]
Ionization smoke detectors were first sold in the United States in 1951; they were used only in major commercial and industrial facilities in the next several years due to their large size and cost.[7] In 1955 simple home "fire detectors" for homes were developed,[8] detecting high temperatures.[9] The United States Atomic Energy Commission (USAEC) granted the first license to distribute smoke detectors using radioactive material in 1963.[5] The first low-cost smoke detector for domestic use was developed by Duane D. Pearsall in 1965, an individual replaceable battery-powered unit that could be easily installed.[10] The "SmokeGard 700"[11] was a beehive-shaped, strong fire-resistant steel unit.[12] The company began mass-producing these units in 1975.[6] Studies in the 1960s determined that smoke detectors respond to fires much faster than heat detectors.[9]
The first single-station smoke detector was invented in 1970 and made public the next year.[9] It was an ionization detector powered by a single 9-volt battery.[9] They cost about US$125 and sold at a rate of a few hundred thousand per year.[7] Several technological developments occurred between 1971 and 1976, including the replacement of cold-cathode tubes with solid-state electronics, which greatly reduced the detectors' sizes and made it possible to monitor battery life.[7] The previous alarm horns, which required specialty batteries, were replaced with horns that were more energy-efficient, enabling the use of commonly available batteries.[7] These detectors could also function with smaller amounts of radioactive source material, and the sensing chamber and smoke detector enclosure were redesigned for more effective operation.[7] The rechargeable batteries were often replaced by a pair of AA batteries along with a plastic shell encasing the detector. The 10-year-lithium-battery-powered smoke alarm was introduced in 1995.[9]
The photoelectric (optical) smoke detector was invented by Donald Steele and Robert Emmark of Electro Signal Lab and patented in 1972.[13]
Design[edit]
Ionization[edit]
Play media
A video overview of how an ionization smoke detector works
Inside a basic ionization smoke detector. The black, round structure at the right is the ionization chamber. The white, round structure at the upper left is the piezoelectric horn that produces the alarm sound.
An americium container from a smoke detector
An ionization smoke detector uses a radioisotope, typically americium-241, to ionize air; a difference due to smoke is detected and an alarm is generated. Ionization detectors are more sensitive to the flaming stage of fires than optical detectors, while optical detectors are more sensitive to fires in the early smouldering stage.[14]
The smoke detector has two ionization chambers, one open to the air, and a reference chamber which does not allow the entry of particles. The radioactive source emits alpha particles into both chambers, which ionizes some air molecules. There is a potential difference (voltage) between pairs of electrodes in the chambers; the electrical charge on the ions allows an electric current to flow. The currents in both chambers should be the same as they are equally affected by air pressure, temperature, and the ageing of the source. If any smoke particles enter the open chamber, some of the ions will attach to the particles and not be available to carry the current in that chamber. An electronic circuit detects that a current difference has developed between the open and sealed chambers, and sounds the alarm.[15] The circuitry also monitors the battery used to supply or back up power, and sounds an intermittent warning when it nears exhaustion. A user-operated test button simulates an imbalance between the ionization chambers, and sounds the alarm if and only if power supply, electronics, and alarm device are functional. The current draw of an ionization smoke detector is low enough for a small battery used as sole or backup power supply to be able to provide power for months or years without the need for external wiring.
Ionization smoke detectors are usually cheaper to manufacture than optical detectors. They may be more prone to false alarms triggered by non-hazardous events than photoelectric detectors,[16][17] and have been found to be much slower to respond to typical house fires.
Americium-241 is an alpha emitter with a half-life of 432.6 years.[18] Alpha particle radiation, as opposed to beta (electron) and gamma (electromagnetic) radiation, is used for two additional reasons: alpha particles have high ionization, so sufficient air particles will be ionized for the current to exist, and they have low penetrative power, meaning they will be stopped, safely, by the plastic of the smoke detector or the air. About one percent of the emitted radioactive energy of 241Am is gamma radiation. The amount of elemental americium-241 is small enough to be exempt from the regulations applied to larger sources. It includes about 37 kBq or 1 µCi of radioactive element americium-241 (241Am), corresponding to about 0.3 µg of the isotope.[19][20] This provides sufficient ion current to detect smoke, while producing a very low level of radiation outside the device.
The americium-241 in ionizing smoke detectors poses a potential environmental hazard, albeit a very small one. Disposal regulations and recommendations for smoke detectors vary from region to region.[21][22] The amount of radioactive material contained in ionizing smoke detectors is very small and thus doesn't represent a significant radiological hazard. If the americium is left in the ionization chamber of the alarm the radiological risk is insignificant because the chamber acts as a shield to the alpha radiation. A person would have to open the sealed chamber and ingest or inhale the americium for the risk to be significant. The radiation risk of exposure to an ionic smoke detector is much smaller than natural background radiation under normal operation.
Some European countries, like France,[23] and some US states and municipalities[24][unreliable source?] have banned the use of domestic ionic smoke alarms because of concerns that they are not reliable enough as compared other technologies.[25] Where an ionizing smoke detector has been the only detector, fires in the early stages have not always been effectively detected.
Photoelectric[edit]
This section needs additional citations for verification. Please help improve this article by adding citations to reliable sources. Unsourced material may be challenged and removed. (August 2016) (Learn how and when to remove this template message)
Optical smoke detector with the cover removed
Optical smoke detector
1: Optical chamber
2: Cover
3: Case moulding
4: Photodiode (transducer)
5: Infrared LED
A photoelectric, or optical smoke detector contains a source of infrared, visible, or ultraviolet light (typically an incandescent light bulb or light-emitting diode), a lens, and a photoelectric receiver (typically a photodiode). In spot-type detectors all of these components are arranged inside a chamber where air, which may contain smoke from a nearby fire, flows. In large open areas such as atria and auditoriums, optical beam or projected-beam smoke detectors are used instead of a chamber within the unit: a wall-mounted unit emits a beam of infrared or ultraviolet light which is either received and processed by a separate device, or reflected back to the receiver by a reflector. In some types, particularly optical beam types, the light emitted by the light source passes through the air being tested and reaches the photosensor. The received light intensity will be reduced due to scattering from particulates of smoke, air-borne dust, or other substances; the circuitry detects the light intensity and generates the alarm if it is below a specified threshold, potentially due to smoke.[26] In other types, typically chamber types, the light is not directed at the sensor, which is not illuminated in the absence of particles. If the air in the chamber contains particles (smoke or dust), the light is scattered and some of it reaches the sensor, triggering the alarm.[26]
According to the National Fire Protection Association (NFPA), "photoelectric smoke detection is generally more responsive to fires that begin with a long period of smoldering". Studies by Texas A&M and the NFPA cited by the City of Palo Alto California state, "Photoelectric alarms react slower to rapidly growing fires than ionization alarms, but laboratory and field tests have shown that photoelectric smoke alarms provide adequate warning for all types of fires and have been shown to be far less likely to be deactivated by occupants."
Although photoelectric alarms are highly effective at detecting smoldering fires and do provide adequate protection from flaming fires, fire safety experts and the National Fire Protection Agency recommend installing what are called combination alarms, which are alarms that either detect both heat and smoke, or use both the ionization and photoelectric processes. Some combination alarms may include a carbon monoxide detection capability.
The type and sensitivity of light source and photoelectric sensor, and type of smoke chamber differ between manufacturers.
Carbon monoxide and carbon dioxide detection[edit]
Carbon monoxide sensors detect potentially fatal concentrations of carbon monoxide gas, which may build up due to faulty ventilation where there are combustion appliances such as gas heaters and cookers, although there is no uncontrolled fire outside the appliance.[27]
High levels of carbon dioxide (CO2) may indicate a fire, and can be detected by a carbon dioxide sensor. Such sensors are often used to measure levels of CO2 which may be undesirable but not indicative of a fire; this type of sensor can also be used to detect and warn of the much higher levels generated by a fire. One manufacturer says that detectors based on CO2 levels are the fastest fire indicators, and also, unlike ionization and optical detectors, detect fires that do not generate smoke, such as those fuelled by alcohol or gasoline. CO2 fire detectors are not susceptible to false alarms due to particles, making them particularly suitable for use in dusty and dirty environments.[28]
Performance differences[edit]
A presentation by Siemens and the Canadian Fire Alarm Association reports the ionization detector as best at detecting incipient-stage fires with invisibly small particles, fast-flaming fires with smaller 0.01-0.4 micron particles, and dark or black smoke, while more modern photoelectric detectors are best at detecting slow-smouldering fires with larger 0.4–10.0 micron particles, and light-coloured white/grey smoke.[29]
Photoelectric smoke detectors respond faster to fire in its early, smouldering stage (before it breaks into flame). The smoke from the smouldering stage of a fire is typically made up of large combustion particles—between 0.3 and 10.0 µm. Ionization smoke detectors respond faster (typically 30–60 seconds) in the flaming stage of a fire. The smoke from the flaming stage of a fire is typically made up of microscopic combustion particles—between 0.01 and 0.3 µm. Also, ionization detectors are weaker in high air-flow environments, and because of this, the photoelectric smoke detector is more reliable for detecting smoke in both the smoldering and flaming stages of a fire.[30]
In June 2006, the Australasian Fire & Emergency Service Authorities Council, the peak representative body for all Australian and New Zealand fire departments, published an official report, 'Position on Smoke Alarms in Residential Accommodation'. Clause 3.0 states, "Ionization smoke alarms may not operate in time to alert occupants early enough to escape from smouldering fires."[31]
In August 2008, the International Association of Fire Fighters (IAFF, with over 300,000 members in North America) passed a resolution recommending the use of photoelectric smoke alarms, saying that changing to photoelectric alarms, "Will drastically reduce the loss of life among citizens and fire fighters."[32]
In May 2011, the Fire Protection Association of Australia's (FPAA) official position on smoke alarms stated, "Fire Prevention Association Australia considers that all residential buildings should be fitted with photoelectric smoke alarms..."[33]
In December 2011, the Volunteer Fire Fighter's Association of Australia published a World Fire Safety Foundation report, 'Ionization Smoke Alarms are DEADLY', citing research outlining substantial performance differences between ionization and photoelectric technology.[34]
In November 2013, the Ohio Fire Chiefs' Association (OFCA) published an official position paper supporting the use of photoelectric technology in Ohioan residences. The OFCA's position states, "In the interest of public safety and to protect the public from the deadly effects of smoke and fire, the Ohio Fire Chiefs' Association endorses the use of Photoelectric Smoke Alarms … In both new construction and when replacing old smoke alarms or purchasing new alarms, we recommend Photoelectric Smoke Alarms."[35]
In June 2014, tests by the North Eastern Ohio Fire Prevention Association (NEOFPA) on residential smoke alarms were broadcast on the ABC's 'Good Morning America' program. The NEOFPA tests showed ionization smoke alarms failing to activate in the early, smoldering stage of fire.[36] The combination ionization-photoelectric alarms failed to activate until an average of over 20 minutes after the stand-alone photoelectric smoke alarms. This vindicated the June 2006 official position of the Australasian Fire & Emergency Service Authorities Council (AFAC) and the October 2008, official position of the International Association of Fire Fighters (IAFF). Both AFAC and the IAFF recommend photoelectric smoke alarms, but not combination ionization/photoelectric smoke alarms.[37]
According to fire tests conformant to EN 54, the CO2 cloud from open fire can usually be detected before particulate.[28]
Due to the varying levels of detection capabilities between detector types, manufacturers have designed multi-criteria devices which cross-reference the separate signals to both rule out false alarms and improve response times to real fires.[30]
Obscuration is a unit of measurement that has become the standard way of specifying smoke detector sensitivity. Obscuration is the effect that smoke has on reducing sensor visibility, expressed in percent obscuration per unit length;[29] higher concentrations of smoke result in higher obscuration levels.
Typical smoke detector obscuration ratings
Detector type
Obscuration
Ionization 2.6–5.0% obs/m (0.8–1.5% obs/ft)[26]
Photoelectric 0.70–13.0% obs/m (0.2–4.0% obs/ft)[26]
Aspirating 0.005–20.5% obs/m (0.0015–6.25% obs/ft)[26]
Laser 0.06–6.41% obs/m (0.02–2.0% obs/ft)[38]
Commercial[edit]
An integrated locking mechanism for commercial building doors. Inside an enclosure are a locking device, smoke detector and power supply.
Commercial smoke detectors are either conventional or addressable, and are connected to security alarm or fire alarm systems controlled by fire alarm control panels (FACP).[39] These are the most common type of detector, and are usually significantly more expensive than single-station battery-operated residential smoke alarms.[39] They are used in most commercial and industrial facilities and other places such as ships and trains,[39] but are also part of some security alarm systems in homes.[40] These detectors don't need to have built in alarms, as alarm systems can be controlled by the connected FACP, which will set off relevant alarms, and can also implement complex functions such as a staged evacuation.[39]
Conventional[edit]
The word "conventional" is slang used to distinguish the method used to communicate with the control unit in newer addressable systems.[39] So called "conventional detectors" are smoke detectors used in older interconnected systems and resemble electrical switches by their way of working.[39] These detectors are connected in parallel to the signaling path so that the current flow is monitored to indicate a closure of the circuit path by any connected detector when smoke or other similar environmental stimulus sufficiently influences any detector.[39] The resulting increase in current flow (or a dead short) is interpreted and processed by the control unit as a confirmation of the presence of smoke and a fire alarm signal is generated.[39] In a conventional system, smoke detectors are typically wired together in each zone and a single fire alarm control panel usually monitors a number of zones which can be arranged to correspond to different areas of a building.[39] In the event of a fire, the control panel is able to identify which zone or zones contain the detector or detectors in alarm, but can not identify which individual detector or detectors are in a state of alarm.[39]
Addressable[edit]
An addressable Simplex Truealarm smoke detector
An addressable system gives each detector an individual number, or address.[39] Addressable systems allow the exact location of an alarm to be plotted on the FACP, while allowing several detectors to be connected to the same zone.[39] In certain systems, a graphical representation of the building is provided on the screen of the FACP which shows the locations of all of the detectors in the building,[39] while in others the address and location of the detector or detectors in alarm are simply indicated.[39]
Addressable systems are usually more expensive than conventional non-addressable systems,[41] and offer extra options, including a custom level of sensitivity (sometimes called Day/Night mode) which can determine the amount of smoke in a given area and contamination detection from the FACP that allows determination of a wide range of faults in detection capabilities of smoke detectors.[39] Detectors become contaminated usually as a result of the build up of atmospheric particulates in the detectors being circulated by the heating and air-conditioning systems in buildings. Other causes include carpentry, sanding, painting, and smoke in the event of a fire.[42] Panels can also be interconnected to monitor a very large number of detectors in multiple buildings.[39] This is most commonly used in hospitals, universities, resorts and other large centres or institutions.[39]
Residential[edit]
Smaller, less expensive, smoke alarm systems, typically used in a domestic/residential environment, may be individual standalone units, or interconnected. They typically generate a loud acoustic warning signal as their only action. Several detectors (whether standalone or interconnected) are normally used in the rooms of a dwelling. There are inexpensive smoke alarms that may be interconnected so that any detector that triggers sounds all alarms. They are powered by mains electricity, with disposable or rechargeable battery backup. They may be interconnected by wires, or wirelessly.They are required in new installations in some jurisdictions.[43]
Several smoke detection methods are used and documented in industry specifications published by Underwriters Laboratories.[44] Alerting methods include:
Audible tones
Usually around 3200 Hz due to component constraints (Audio advancements for persons with hearing impairments have been made)
85 dBA loudness at 10 feet
Spoken voice alert
Visual strobe lights
177 candela output
Tactile stimulation (e.g. bed or pillow shaker), although no standards existed as of 2008 for tactile stimulation alarm devices.
Some models have a hush or temporary silence feature that allows silencing, typically by pressing a button on the housing, without removing the battery. This is especially useful in locations where false alarms can be relatively common (e.g. near a kitchen), or users might remove the battery permanently to avoid the annoyance of false alarms, preventing the alarm from detecting a fire should one break out.
While current technology is very effective at detecting smoke and fire conditions, the deaf and hard of hearing community has raised concerns about the effectiveness of the alerting function in awakening sleeping individuals in certain high-risk groups such as the elderly, those with hearing loss and those who are intoxicated.[45] Between 2005 and 2007 research sponsored by the United States' National Fire Protection Association (NFPA) focused on understanding the cause of the higher number of deaths in such high-risk groups. Initial research into the effectiveness of the various alerting methods is sparse. Research findings suggest that a low frequency (520 Hz) square wave output is significantly more effective at awakening high risk individuals. Wireless smoke and carbon monoxide detectors linked to alert mechanisms such as vibrating pillow pads for the hearing impaired, strobes, and remote warning handsets are more effective at waking people with serious hearing loss than other alarms.[46]
Batteries[edit]
Batteries are used either as sole or as backup power for residential smoke detectors. Mains-operated detectors have disposable or rechargeable batteries; others run only on 9-volt disposable batteries. When the battery is exhausted a battery-only smoke detector becomes inactive; most smoke detectors chirp repeatedly if the battery is low. It has been found that battery-powered smoke detectors in many houses have dead batteries. It has been estimated[when?] that in the UK over 30% of smoke alarms may have dead or removed batteries. In response public information campaigns have been created to remind people to change smoke detector batteries regularly. In Australia, for example, a public information campaign suggests that smoke alarm batteries should be replaced on April Fools' Day every year.[47] In regions using daylight saving time, campaigns may suggest that people change their batteries when they change their clocks or on a birthday.
Some mains-powered detectors are fitted with a non-rechargeable lithium battery for backup with a life of typically ten years, after which it is recommended that the detector be replaced. User-replaceable disposable 9-volt lithium batteries, which last at least twice as long as alkaline batteries are available.
The US National Fire Protection Association recommends that home-owners replace smoke detector batteries with a new battery at least once per year, when it starts chirping (a signal that the battery is low), or when it fails a test, which the NFPA recommends to be carried out at least once per month by pressing the "test" button on the alarm.[48]
Reliability[edit]
A 2004 NIST report concluded that "Smoke alarms of either the ionization type or the photoelectric type consistently provided time for occupants to escape from most residential fires," and, "Consistent with prior findings, ionization type alarms provided somewhat better response to flaming fires than photoelectric alarms (57 to 62 seconds faster response), and photoelectric alarms provided (often) considerably faster response to smoldering fires than ionization type alarms (47 to 53 minutes faster response)."[17]
Regular cleaning can prevent false alarms caused by the build-up of dust and insects, particularly on optical type alarms as they are more susceptible to these factors. A vacuum cleaner can be used to clean domestic smoke detectors to remove detrimental dust. Optical detectors are less susceptible to false alarms in locations such as near a kitchen producing cooking fumes.[49]
On the night of May 31, 2001, Bill Hackert and his daughter Christine of Rotterdam, New York died when their house caught fire and a First Alert ionization smoke detector failed to sound.[50] The cause of the fire was a frayed electrical cord behind a couch that smoldered for hours before engulfing the house with flames and smoke.[50] The ionization smoke detector was found to be defectively designed, and in 2006 a jury in the United States District Court for the Northern District of New York decided that First Alert and its then parent company, BRK Brands, was liable for millions of dollars in damages.[50]
Installation and placement[edit]
A 2007 U.S. guide to placing smoke detectors, suggesting that one be placed on every floor of a building, and in each bedroom
In the United States most state and local laws regarding the required number and placement of smoke detectors are based upon standards established in NFPA 72, National Fire Alarm and Signaling Code.[51] Laws governing the installation of smoke detectors vary depending on the locality. However, some rules and guidelines for existing homes are relatively consistent throughout the developed world. For example, Canada and Australia require a building to have a working smoke detector on every level. The United States NFPA code cited in the previous paragraph requires smoke detectors on every habitable level and within the vicinity of all bedrooms. Habitable levels include attics that are tall enough to allow access.[51] Many other countries have comparable requirements.
In new construction, minimum requirements are typically more stringent. All smoke detectors must be hooked directly to the electrical wiring, be interconnected and have a battery backup. In addition, smoke detectors are required either inside or outside every bedroom, depending on local codes. Smoke detectors on the outside will detect fires more quickly, assuming the fire does not begin in the bedroom, but the sound of the alarm will be reduced and may not wake some people. Some areas also require smoke detectors in stairways, main hallways and garages.[52]
A dozen or more detectors may be connected via wiring or wirelessly such that if one detects smoke, the alarms will sound on all the detectors in the network, improving the likelihood that occupants will be alerted even if smoke is detected far from their location. Wired interconnection are more practical in new construction than for existing buildings.
In the UK the installation of smoke alarms in new builds must comply with British Standard BS5839 pt6. BS 5839: Pt.6: 2004 recommends that a new-build property consisting of no more than 3 floors (less than 200 square metres per floor) should be fitted with a Grade D, LD2 system. Building Regulations in England, Wales and Scotland recommend that BS 5839: Pt.6 should be followed, but as a minimum a Grade D, LD3 system should be installed. Building Regulations in Northern Ireland require a Grade D, LD2 system to be installed, with smoke alarms fitted in the escape routes and the main living room and a heat alarm in the kitchen; this standard also requires all detectors to have a mains supply and a battery back up.[53]
Standards[edit]
EN54 European standards[edit]
Fire detection products have the European Standard EN 54 Fire Detection and Fire Alarm Systems that is a mandatory standard for every product that is going to be delivered and installed in any country in the European Union (EU). EN 54 part 7 is the standard for smoke detectors. European standard are developed to allow free movement of goods in the European Union countries. EN 54 is widely recognized around the world. The EN 54 certification of each device must be issued annually.[54] [55]
Coverage of smoke and temperature detectors with European standard EN54[edit]
Surface area (square metres)
Type of detector
Height (m)
Ceiling slope ≤20°
Ceiling slope >20°
Smax(square metres)
Rmax (m)
Smax (square metres)
Rmax(m)
SA ≤80 EN54-7 ≤12 80 6,6 80 8,2
SA >80 EN54-7 ≤6 60 5,7 90 8,7
6< h ≤ 12 80 6,6 110 9,6
SA ≤30 EN54-5 Clase A1 ≤7,5 30 4,4 30 5,7
EN54-5 Clase A2,B,C,D,F,G ≤ 6 30 4,4 30 5,7
SA >30 EN54-5 Clase A1 ≤7,5 20 3,5 40 6,5
EN54-5 Clase A2,B,C,D,E,F,G ≤6 20 3,5 40 6,5
EN54-7: Smoke detector
EN54-5: Temperature detector
SA: Surface area
Smax (square metres): Maximum surface coverage
Rmax (m): Maximum radio
Information in "bold" is the standard coverage of the detector. Smoke detector coverage is 60 square metres and temperature smoke detector coverage is 20 square metres. Height from ground is an important issue for a correct protection.[56]
Australia and United States[edit]
In the United States, the first standard for home smoke alarms, NFPA 74, was established in 1967.[9] In 1969, the AEC allowed homeowners to use smoke detectors without a license.[5] The Life Safety Code (NFPA 101), passed by the National Fire Protection Association in 1976, first required smoke alarms in homes.[9] Smoke alarm sensitivity requirements in UL 217 were modified in 1985 to reduce susceptibility to nuisance alarms.[9] In 1988 BOCA, ICBO, and SBCCI model building codes begin requiring smoke alarms to be interconnected and located in all sleeping rooms.[9] In 1989 NFPA 74 first required smoke alarms to be interconnected in every new home construction, and in 1993 NFPA 72 first required that smoke alarms be placed in all bedrooms.[9] NFPA began requiring the replacement of smoke detectors after ten years in 1999.[9] In 1999 Underwriters Laboratory changed smoke alarm labeling requirements so that all smoke alarms must have a manufactured date written in Plain English.
In June 2013 a World Fire Safety Foundation report titled, 'Can Australian and U.S. Smoke Alarm Standards be Trusted?' was published in the official magazine of the Australian Volunteer Fire Fighter's Association. The report brings into question the validity of testing criteria used by American and Australian government agencies when undergoing scientific testing of ionization smoke alarms in smoldering fires.[57]
Legislation[edit]
In June 2010 the City of Albany, California enacted photoelectric-only legislation after a unanimous decision by the Albany City Council; several other Californian and Ohioan cities enacted similar legislation shortly afterwards.[58]
In November 2011 the Northern Territory enacted Australia's first residential photoelectric legislation mandating the use of photoelectric smoke alarms in all new Northern Territory homes.[59]
In the Australian State of Queensland, from 1 January 2017 all smoke alarms in new dwellings (or where a dwelling is substantially renovated) must be photoelectric, not also contain an ionisation sensor, be hardwired to the mains power supply with a secondary power source (i.e. battery) and be interconnected with every other smoke alarm in the dwelling so all activate together. From that date, all replacement smoke alarms must be photoelectric.
From 1 January 2022, all dwellings sold, leased or where a lease is renewed must comply as for new dwellings.
From 1 January 2027, all dwellings must comply as for new dwellings.[60]
In June 2013, in an Australian Parliamentary speech, the question was asked, "Are ionization smoke alarms defective?" This was further to the Australian Government's scientific testing agency (the Commonwealth Scientific and Industrial Research Organisation - CSIRO) data revealing serious performance problems with ionization technology in the early, smoldering stage of fire, a rise in litigation involving ionization smoke alarms, and increasing legislation mandating the installation of photoelectric smoke alarms. The speech cited a May 2013, World Fire Safety Foundation report published in the Australian Volunteer Fire Fighter Association's magazine titled, 'Can Australian and U.S. Smoke Alarm Standards be Trusted?' The speech concluded with a request for one of the world's largest ionization smoke alarm manufacturers and the CSIRO to disclose the level of visible smoke required to trigger the manufacturers' ionization smoke alarms under CSIRO scientific testing.[61] The US state of California banned the sale of smoke detectors with replaceable batteries [62]
References[edit]
Jump up ^ "Smoke Alarms in U.S. Home Fires". nfpa.org. September 2015. Retrieved 2017-07-28.
Jump up ^ US 436961, Francis Robbins Upton
Jump up ^ "Birthday Party to Edison; Men Associated with Him in the Early 80s Organize the Pioneers" (PDF). The New York Times. The New York Times Company. February 3, 1918. Retrieved January 13, 2011. Francis R. Upton of Newark, Mr. Edison's oldest associate, has been elected President of the Pioneers.
Jump up ^ Prosser, Richard. Birmingham Inventors And Inventions. H.M. Patent Office (originally 1881) later published by S.R. Publishers 1970. ISBN 0-85409-578-0.
^ Jump up to: a b c d e "NRC: Fact Sheet on Smoke Detectors". NRC.gov. United States Nuclear Regulation Commission. 4 September 2013. Retrieved 9 June 2014.
^ Jump up to: a b c d Wallis, Ian (1 November 2013). 50 Best Business Ideas That Changed the World. Jaico Publishing House. ISBN 9788184952841. Retrieved 2014-11-20.
^ Jump up to: a b c d e f g "How smoke detector is made". MadeHow.com. Advameg. Retrieved 9 June 2014.
Jump up ^ Jones, Hilton Ira (April 1955). "Peeps at Things to Come". The Rotarian. Rotary International. 86 (4). Retrieved 2014-11-27.
^ Jump up to: a b c d e f g h i j k White Paper: Home Smoke Alarms and Other Fire Detection and Alarm Equipment (Technical report). Public/Private Fire Safety Council. 2006. 1.
Jump up ^ Ha, Peter (25 October 2010). "Smoke Detector". Time. Time (ALL-TIME 100 Gadgets): 1. Retrieved 9 June 2014.
Jump up ^ Voluntary Standards and Accreditation Act of 1977, Act No. S. 825 of 1 March 1977 (in English). Retrieved on 24 July 2014.
Jump up ^ David Lucht (1 March 2013). "Where Theres Smoke". Nfpa.org. Retrieved 7 January 2016. With picture of SmokeGard
Jump up ^ US patent 3863076, Donald F. Steele & Robert B. Enemark, "Optical Smoke Detector", issued 1975-01-28
Jump up ^ Fleming, Jay. "Smoke Detector Technology Research", retrieved 2011-11-07
Jump up ^ Cote, Arthur; Bugbee, Percy (1988). "Ionization smoke detectors". Principles of fire protection. Quincy, MA: National Fire Protection Association. p. 249. ISBN 0-87765-345-3.
Jump up ^ Residential Smoke Alarm Performance, Thomas Cleary, Building and Fire Research Laboratory, National Institute of Standards and Technology, UL Smoke and Fire Dynamics Seminar. November, 2007.
^ Jump up to: a b "Performance of Home Smoke Alarms Analysis of the Response of Several Available Technologies in Residential Fire Settings". Bukowski, Cleary et al.
Jump up ^ "NuDat 2.1 database". NNDC.BNL.gov. Brookhaven National Laboratory.
Jump up ^ "Smoke detectors and americium-241 fact sheet" (PDF). Canadian Nuclear Society. Retrieved 2009-08-31.
Jump up ^ Gerberding, Julie Louise (April 2004). "Toxicological Profile for Americium" (PDF; 2.1MiB). United States Department of Health and Human Services/Agency for Toxic Substances and Disease Registry. Retrieved 2009-08-29.
Jump up ^ "Disposing of Smoke Detectors | Radiation Protection | US EPA". EPA. 27 June 2012. Retrieved 2013-06-26.
Jump up ^ "Safe disposal of smoke alarms - Fire and Rescue NSW". NSW Government. 26 November 2012. Retrieved 2013-06-26.
Jump up ^ "Lycée Blaise Pascal Rouen - Smoke alarms". pascal-lyc.spip.ac-rouen.fr. Retrieved 2015-12-28.
Jump up ^ "Ionization Smoke Detector Injury Attorney | Bruning Legal". www.bruninglegal.com. Retrieved 2015-12-28.
Jump up ^ "Smoke Alarms in the Home" (PDF). CFPA-E.eu. Confederation of Fire Protection Associations in Europe. 2008. p. 5. Retrieved 2015-05-11.
^ Jump up to: a b c d e Brazzell, D. "The Effects of High Air Velocity and Complex Airflow Patterns on Smoke Detector Performance" (PDF). AFCOM8-21.AFCOM-Miami-Admin.com. Archived from the original (PDF) on 2012-03-20. Retrieved 2009-05-13.
Jump up ^ New York City Fire Department. "Carbon monoxide alarms" (PDF). Retrieved 2012-05-28.
^ Jump up to: a b "CO2 is an excellent fire indicator" (PDF). senseair.se. p. 4. Retrieved 2012-08-18.
^ Jump up to: a b Smoke Detector Sensitivity testing: Siemens and Canadian Fire Alarm Association
^ Jump up to: a b "Fire and Life Safety in Mission-Critical Applications". Life Safety Magazine. Archived from the original on April 16, 2012. Retrieved 2011-07-01. [not in citation given]
Jump up ^ "Position on Smoke Alarms in Residential Accommodation" (PDF). Australasian Fire & Emergency Service Authorities Council. Retrieved 2006-06-01.
Jump up ^ "International Association of Fire Fighters Resolution 15". The International Association of Fire Fighters, California, USA. Retrieved 2013-06-27.
Jump up ^ "Position Statement - Selection of Residential Smoke Alarms - clause 5.0, page 7, May, 2011" (PDF). Fire Protection Association Australia. Retrieved 2013-06-27.
Jump up ^ "Ionization Smoke Alarms Are DEADLY". The World Fire Safety Foundation. Retrieved 2001-06-27.
Jump up ^ "OFCA Position Statement on Smoke Alarms" (PDF). Ohio Fire Chief's Association. Retrieved 2014-10-03.
Jump up ^ "'GMA' Investigates: Will Your Smoke Detector Respond Fast Enough?". Good Morning America. Retrieved 2014-05-29.
Jump up ^ "Smoke Alarm Myths Explained". The World Fire Safety Foundation. Retrieved 2014-09-03.
Jump up ^ "Low-Profile Plug-in Intelligent Laser Smoke Detector" (PDF). SystemSensor.com. Retrieved 2014-05-01.
^ Jump up to: a b c d e f g h i j k l m n o p q Fire Alarm System
Jump up ^ Fisher, Jeff. "Adding Smoke Detectors to a Security System". Wiki.hometech.com. TechWiki. Retrieved 6 June 2014.
Jump up ^ "Addressable Equipment". Westminster International Ltd. Retrieved 2010-06-09.
Jump up ^ "Contaminated (dirty) Smoke Detectors". Firewize.com. Firewize Holdings Pty. 2012. Retrieved 6 June 2014.
Jump up ^ Nest Labs (17 June 2015). "Why are interconnected smoke alarms better than standalone smoke alarms?". Nest Web site. Retrieved 7 January 2016.
Jump up ^ Underwriters Laboratories 217. "Single and Multiple Station Smoke Alarms, UL 1971: Signaling Devices for the Hearing Impaired, UL 268: Smoke Detectors for Fire Alarm Signaling Systems".
Jump up ^ Alarm concern from the Hearing Loss Association of America
Jump up ^ Hearing Loss Web discusses current low frequency alarms for hard of hearing.
Jump up ^ Beacham, Janine. "Don't be a fool: change alarm batteries". Augusta Margaret River Mail. Retrieved 19 April 2011.
Jump up ^ "SMOKE ALARM SAFETY TIPS". Safety Information. National Fire Protection Association. Retrieved 2009-05-17.
Jump up ^ "Cleaning Smoke and Heat Alarms". SDFireAlarms.co.uk. Hav Direct. 2011. Retrieved 2015-07-31.
^ Jump up to: a b c Segall, Bob (April 2, 2008). "Federal appeals court upholds $2.8M award for faulty smoke alarm". WTHR.com. WTHR. Retrieved 2008-10-28.
^ Jump up to: a b NFPA 72, Act No. 72-2013 of 2013 (in English). Retrieved on 6 August 2014.
Jump up ^ Fletcher, Gregory (18 May 2011). Residential Construction Academy: House Wiring. Technology & Engineering. ISBN 978-1111306212. Retrieved 24 November 2014.
Jump up ^ BS 5839-6:2013 Fire detection and fire alarm systems for buildings - Code of practice for the design, installation, commissioning and maintenance of fire detection and fire alarm systems in domestic premises, Act No. 5839-6 of 2013 (in Uk english). Retrieved on 24 November 2014.
Jump up ^ "CEN - Technical Bodies". Cen.eu. 2012-11-11. Retrieved 2014-08-22.
Jump up ^ "BS EN 54-11:2001 - Fire detection and fire alarm systems. Manual call points – BSI British Standards". Shop.bsigroup.com. Retrieved 2014-08-22.
Jump up ^ http://www.aenor.es/DOCUMENTOS/NORMALIZACION/NORMASNACIONALES/EXTRACTOS/(EX)UNE_23007-14=2009.pdf
Jump up ^ "Can Australian and U.S. Smoke Alarm Standards be Trusted?". The World Fire Safety Foundation. Retrieved 2013-06-27.
Jump up ^ "Albany, California Ordinance 2010-06 Photoelectric Specific Requirements". The Albany City Council, Albany, California, USA. Retrieved 2013-06-27.
Jump up ^ "Northern Territory Photoelectric smoke alarm legislation". Northern Territory Fire & Rescue Service. Retrieved 2001-06-27.
Jump up ^ https://www.qfes.qld.gov.au/community-safety/smokealarms/Documents/New-Smoke-Alarm-Legislation.pdf
Jump up ^ "Smoke Alarms". Hansard - Mr Christopher Gulaptis MP, Private Member's Statements, New South Wales Parliamentary Debates, Legislative Assembly, New South Wales, Australia 20 June 2013, pp.22218. Retrieved 2013-06-26.
Jump up ^ http://abc7news.com/news/law-bans-sale-of-smoke-detectors-with-replaceable-batteries/891576/
External links[edit]
Wikimedia Commons has media related to Smoke detector.
Smoke alarm research from the national institute of Standards and Technology
Report from the UL smoke alarm STP research group
"Teardown of a Photoelectric Smoke Detector". BigClivedotcom (YouTube). 2015-09-25. - Examination of a Generic Brand photoelectric Smoke Detector.
[show]
v
t
e
Fire protection
General
Active fire protection
Passive fire protection
Fire suppression
Manual
Fire blanket
Fire bucket
Fire extinguisher
Automatic
Condensed aerosol fire suppression
Fire sprinkler system
Fire sprinkler
Gaseous fire suppression
Detection
Flame detector
Heat detector
Smoke detector
Notification
Drill
Fire alarm system
Call box
Control panel
Notification appliance
Pull station/call point
Smoke detector
Awards
Arthur B. Guise Medal
Harry C. Bigglestone Award
Category
Commons
[show]
v
t
e
Firefighting
Personnel
Fire captain
Fire chief
Fire marshal
Fire police
Handcrew
Station officer
Volunteer fire department
Women in firefighting
Facilities
Fire department
List of fire departments
Fire lookout tower
Fire station
Apparatus
Airport crash tender
Fire bike
Fire chief's vehicle
Fire engine
Firefighting apparatus
HazMat
Heavy rescue
Light and air
Quint
Tender
Wildland tender
Wildland engine
Equipment
Bunker gear
Escape chair
Fire extinguisher
Fire hose
Fire hydrant
Fire retardant
Fire shelter
Fireman's pole
Fireman's switch
Flame retardant
Fog nozzle
Halligan bar
Hard suction hose
Hazmat suit
Heat detector
Hose bridge
Hydraulic rescue tools ("Jaws of life")
Nomex
PASS
Proximity suit
SCBA
Siren
Smoke detector
Thermal imaging camera
Terminology
Backdraft
Dead man zone
Deluge gun
Draft
Fire classes
Fire control
Fire safety
Fire triangle
Fireman's carry
Firewall
Flash fire
Forcible entry
Gaseous fire suppression
Stop, drop and roll
Structure fire
Two-in, two-out
Ventilation
Miscellaneous
Fire camp
Fire engine red
Fire photography
Fire protection engineering
Foam
Geography of firefighting
History of firefighting
International Association of Fire Fighters
International Firefighters' Day
List of firefighting films
Muster
Saint Florian
World Firefighters Games
World Police and Fire Games
Wildland
firefighting
Equipment
and
tactics
Aerial firefighting
Controlled burn
Driptorch
Fire hose
Fire lookout tower
Fire retardant
Fire retardant gel
Fire trail
Firebreak
Firefighting apparatus
Firefighting foam
Helicopter bucket
Hose pack
MAFFS
Pulaski
Wildland fire engine
Wildland water tender
Wildfire suppression equipment and personnel
Personnel
Engine crew
Handcrew
Helitack
Hotshots
Lookout
Smokejumper
By location
Australia
United States (California, Washington)
Lists
Glossary of wildfire terms
List of wildfires
Category
Commons
[show]
v
t
e
Sensors
Acoustic, sound, vibration
Geophone
Hydrophone
Microphone
Seismometer
Automotive, transportation
Air–fuel ratio meter
Blind spot monitor
Crankshaft position sensor
Curb feeler
Defect detector
Engine coolant temperature sensor
Hall effect sensor
MAP sensor
Mass flow sensor
Omniview technology
Oxygen sensor
Parking sensors
Radar gun
Speed sensor
Speedometer
Throttle position sensor
Tire-pressure monitoring system
Torque sensor
Transmission fluid temperature sensor
Turbine speed sensor
Variable reluctance sensor
Vehicle speed sensor
Water sensor
Wheel speed sensor
Chemical
Breathalyzer
Carbon dioxide sensor
Carbon monoxide detector
Catalytic bead sensor
Chemical field-effect transistor
Electrochemical gas sensor
Electrolyte–insulator–semiconductor sensor
Electronic nose
Fluorescent chloride sensors
Holographic sensor
Hydrocarbon dew point analyzer
Hydrogen sensor
Hydrogen sulfide sensor
Infrared point sensor
Ion selective electrode
Microwave chemistry sensor
Nitrogen oxide sensor
Nondispersive infrared sensor
Olfactometer
Optode
Oxygen sensor
Pellistor
pH glass electrode
Potentiometric sensor
Redox electrode
Smoke detector
Zinc oxide nanorod sensor
Electric, magnetic, radio
Current sensor
Electroscope
Galvanometer
Hall effect sensor
Hall probe
Magnetic anomaly detector
Magnetometer
MEMS magnetic field sensor
Metal detector
Planar Hall sensor
Radio direction finder
Test light
Environment, weather,
moisture
Actinometer
Bedwetting alarm
Ceilometer
Dew warning
Electrochemical gas sensor
Fish counter
Frequency domain sensor
Gas detector
Hook gauge evaporimeter
Humistor
Hygrometer
Leaf sensor
Psychrometer
Pyranometer
Pyrgeometer
Rain gauge
Rain sensor
SNOTEL
Snow gauge
Soil moisture sensor
Stream gauge
Tide gauge
Weather radar
Flow, fluid velocity
Air flow meter
Anemometer
Flow sensor
Gas meter
Mass flow sensor
Water metering
Ionising radiation,
subatomic particles
Bubble chamber
Cloud chamber
Geiger–Müller tube
Geiger counter
Ionization chamber
Neutron detection
Particle detector
Proportional counter
Scintillation counter
Semiconductor detector
Scintillator
Thermoluminescent dosimeter
Wire chamber
Navigation instruments
Airspeed indicator
Machmeter
Altimeter
Attitude indicator
Depth gauge
Fluxgate compass
Gyroscope
Inertial navigation system
Inertial reference unit
Magnetic compass
MHD sensor
Ring laser gyroscope
Turn coordinator
Variometer
Vibrating structure gyroscope
Yaw-rate sensor
Position, angle,
displacement
Accelerometer
Angular rate sensor
Auxanometer
Capacitive displacement sensor
Capacitive sensing
Gravimeter
Inclinometer
Integrated circuit piezoelectric sensor
Laser rangefinder
Laser surface velocimeter
Lidar
Linear encoder
Linear variable differential transformer
Liquid capacitive inclinometers
Odometer
Photoelectric sensor
Piezoelectric accelerometer
Position sensor
Rotary encoder
Rotary variable differential transformer
Selsyn
Sudden Motion Sensor
Tachometer
Tilt sensor
Ultrasonic thickness gauge
Variable reluctance sensor
Velocity receiver
Optical, light, imaging
Active pixel sensor
Angle–sensitive pixel
Back-illuminated sensor
Charge-coupled device
Contact image sensor
Electro-optical sensor
Flame detector
Infrared
Kinetic inductance detector
LED as light sensor
Light-addressable potentiometric sensor
Nichols radiometer
Optical fiber
Photodetector
Photodiode
Photoelectric sensor
Photoionization detector
Photomultiplier
Photoresistor
Photoswitch
Phototransistor
Phototube
Position sensitive device
Scintillometer
Shack–Hartmann wavefront sensor
Single-photon avalanche diode
Superconducting nanowire single-photon detector
Transition edge sensor
Tristimulus colorimeter
Visible-light photon counter
Wavefront sensor
Pressure
Barograph
Barometer
Boost gauge
Bourdon gauge
Hot-filament ionization gauge
Ionization gauge
McLeod gauge
Oscillating U-tube
Permanent Downhole Gauge
Piezometer
Pirani gauge
Pressure gauge
Pressure sensor
Tactile sensor
Time pressure gauge
Force, density, level
Bhangmeter
Force gauge
Hydrometer
Level sensor
Load cell
Magnetic level gauge
Nuclear density gauge
Piezoelectric sensor
Strain gauge
Torque sensor
Viscometer
Thermal, heat,
temperature
Bimetallic strip
Bolometer
Calorimeter
Exhaust gas temperature gauge
Flame detection
Gardon gauge
Golay cell
Heat flux sensor
Infrared thermometer
Microbolometer
Microwave radiometer
Net radiometer
Quartz thermometer
Resistance thermometer
Silicon bandgap temperature sensor
Special sensor microwave/imager
Thermistor
Thermocouple
Thermometer
Proximity, presence
Alarm sensor
Doppler radar
Motion detector
Occupancy sensor
Passive infrared sensor
Proximity sensor
Reed switch
Stud finder
Touch switch
Triangulation sensor
Wired glove
Sensor technology
Active pixel sensor
Back-illuminated sensor
Biochip
Biosensor
Capacitance probe
Carbon paste electrode
Catadioptric sensor
Digital sensors
Displacement receiver
Electromechanical film
Electro-optical sensor
Fabry–Pérot interferometer
Fisheries acoustics
Image sensor
Image sensor format
Inductive sensor
Intelligent sensor
Lab-on-a-chip
Leaf sensor
Machine vision
Microelectromechanical systems
Photoelasticity
Quantum sensor
Radar
Ground-penetrating radar
Synthetic aperture radar
Radar tracker
Sensor array
Sensor fusion
Sensor grid
Sensor node
Soft sensor
Sonar
Staring array
Transducer
Ultrasonic sensor
Video sensor technology
Visual sensor network
Wheatstone bridge
Wireless sensor network
Related
List of sensors
Retrieved from "https://en.wikipedia.org/w/index.php?title=Smoke_detector&oldid=827515317"
Categories:
Active fire protection
American inventions
Detectors
Fire detection and alarm
Hidden categories:
CS1: Julian–Gregorian uncertainty
All articles with failed verification
Articles with failed verification from July 2016
All articles lacking reliable references
Articles lacking reliable references from December 2017
Articles needing additional references from August 2016
All articles needing additional references
All articles with vague or ambiguous time
Vague or ambiguous time from January 2016
Articles containing video clips
Navigation menu
Personal tools
Not logged in
Talk
Contributions
Create account
Log in
Namespaces
Article
Talk
Variants
Views
Read
Edit
View history
More
Search
Navigation
Main page
Contents
Featured content
Current events
Random article
Donate to Wikipedia
Wikipedia store
Interaction
Help
About Wikipedia
Community portal
Recent changes
Contact page
Tools
What links here
Related changes
Upload file
Special pages
Permanent link
Page information
Wikidata item
Cite this page
Print/export
Create a book
Download as PDF
Printable version
In other projects
Wikimedia Commons
Languages
العربية
Català
Čeština
Dansk
Deutsch
Eesti
Español
فارسی
Français
한국어
Bahasa Indonesia
Italiano
Nederlands
日本語
Norsk
Norsk nynorsk
Polski
Português
Română
Русский
Simple English
Slovenščina
Српски / srpski
Suomi
Svenska
தமிழ்
తెలుగు
Türkçe
Українська
Võro
Winaray
粵語
23 more
Edit links
This page was last edited on 25 February 2018, at 04:26.
Text is available under the Creative Commons Attribution-ShareAlike License; additional terms may apply. By using this site, you agree to the Terms of Use and Privacy Policy. Wikipedia® is a registered trademark of the Wikimedia Foundation, Inc., a non-profit organization.
Privacy policy
About Wikipedia
Disclaimers
Contact Wikipedia
Developers
Cookie statement
Mobile view
Enable previews

value: mw-page-base noprint

value: mw-head-base noprint

value: firstHeading firstHeading en

value: siteSub noprint

value: jump-to-nav mw-jump

attr: href class title

attr: class style

tag: b

value: /wiki/Alarm mw-redirect Alarm

tag: p

value: <video id="mwe_player_1" poster="//upload.wikimedia.org/wikipedia/commons/thumb/0/07/Smoke-engineerguy.ogv/534px--Smoke-engineerguy.ogv.jpg" controls="" preload="none" autoplay="" style="width:534px;height:300px" class="kskin" data-durationhint="224.14222222222" data-startoffset="0" data-mwtitle="Smoke-engineerguy.ogv" data-mwprovider="wikimediacommons"><source src="//upload.wikimedia.org/wikipedia/commons/0/07/Smoke-engineerguy.ogv" type="video/ogg; codecs="theora, vorbis"" data-title="Original Ogg file, 534 × 300 (617 kbps)" data-shorttitle="Ogg source" data-width="534" data-height="300" data-bandwidth="617040" data-framerate="29.97"/><source src="//upload.wikimedia.org/wikipedia/commons/transcoded/0/07/Smoke-engineerguy.ogv/Smoke-engineerguy.ogv.160p.webm" type="video/webm; codecs="vp8, vorbis"" data-title="Low bandwidth WebM (160P)" data-shorttitle="WebM 160P" data-transcodekey="160p.webm" data-width="284" data-height="160" data-bandwidth="185216" data-framerate="29.97"/><source src="//upload.wikimedia.org/wikipedia/commons/transcoded/0/07/Smoke-engineerguy.ogv/Smoke-engineerguy.ogv.240p.webm" type="video/webm; codecs="vp8, vorbis"" data-title="Small WebM (240P)" data-shorttitle="WebM 240P" data-transcodekey="240p.webm" data-width="426" data-height="240" data-bandwidth="261456" data-framerate="29.97"/></video>

value:
/wiki/Potential_difference
mw-redirect
Potential difference

value:
/wiki/Electrical_charge
mw-redirect
Electrical charge

value:
/wiki/Gamma_radiation
mw-redirect
Gamma radiation

value: The material near this tag may rely on an unreliable source. (December 2017)

value: Help:Introduction to referencing with Wiki Markup/1

value: plainlinks metadata ambox ambox-content ambox-Refimprove

value: Edit section: Carbon monoxide and carbon dioxide detection

value:
/wiki/Carbon_monoxide_sensor
mw-redirect
Carbon monoxide sensor

value: International Association of Fire Fighters

value:
/wiki/Underwriters_Laboratories
mw-redirect
Underwriters Laboratories

value: The time period mentioned near this tag is ambiguous. (January 2016)

value: Wikipedia:Manual of Style/Dates and numbers

value: Edit section: Installation and placement

value:
/wiki/Battery_backup
mw-redirect
Battery backup

value:
/wiki/Garage_(house)
mw-redirect
Garage (house)

value: Edit section: Coverage of smoke and temperature detectors with European standard EN54

value: Edit section: Australia and United States

value: Building Officials Code Administrators International

value: International Conference of Building Officials

value: Southern Building Code Congress International

value:
nofollow
http://www.nndc.bnl.gov/nudat2/
external text

value: Agency for Toxic Substances and Disease Registry

value: United States Environmental Protection Agency

value: The material near this tag failed verification of its source citation(s). (July 2016)

value: -moz-column-width: 30em; -webkit-column-width: 30em; column-width: 30em; list-style-type: decimal;

value:
col
navbox-title
3
background:red; color:white

value: background:red; color:white;width:1%;background: transparent; color:black; -moz-box-shadow: inset 1px 1px 0 red, inset -1px -1px 0 red; -webkit-box-shadow: inset 1px 1px 0 red, inset -1px -1px 0 red; box-shadow: inset 1px 1px 0 red, inset -1px -1px 0 red;

value:
navbox-image
5
width:1px;padding:0px 0px 0px 2px

value: width:1%;background: transparent; -moz-box-shadow: inset 1px 1px 0 red, inset -1px -1px 0 red; -webkit-box-shadow: inset 1px 1px 0 red, inset -1px -1px 0 red; box-shadow: inset 1px 1px 0 red, inset -1px -1px 0 red;

attr: alt src title width height srcset data-file-width data-file-height

value: color: white; text-decoration: inherit; -moz-text-decoration-color: white; text-decoration-color: white;

value:
navbox-abovebelow
3
background:red; color:white

value: nowraplinks hlist collapsible autocollapse navbox-inner

value: ;background: #CE2029; color: white;;background:none transparent;border:none;-moz-box-shadow:none;-webkit-box-shadow:none;box-shadow:none;

value:
col
navbox-title
2
background: #CE2029; color: white;

value: width:1%;background: #e5575f; color: white;

value: width:1%;background: #ea797f; color: white;

value: Wildfire suppression equipment and personnel

value:
navbox-abovebelow
2
background: #CE2029; color: white;

value: navigation navbox Firefighting padding:3px

value:
/wiki/Engine_coolant_temperature_sensor
mw-redirect
Engine coolant temperature sensor

value:
/wiki/Parking_sensors
mw-redirect
Parking sensors

value:
/wiki/PH_glass_electrode
mw-redirect
PH glass electrode

value:
/wiki/Redox_electrode
mw-redirect
Redox electrode

value:
/wiki/Flow_sensor
mw-redirect
Flow sensor

value:
/wiki/Magnetic_compass
mw-redirect
Magnetic compass

value:
/wiki/Turn_coordinator
mw-redirect
Turn coordinator

value: Linear variable differential transformer

value: Rotary variable differential transformer

value:
/wiki/Tilt_sensor
mw-redirect
Tilt sensor

value:
/wiki/LED_as_light_sensor
mw-redirect
LED as light sensor

value: Superconducting nanowire single-photon detector

value:
/wiki/Transition_edge_sensor
mw-redirect
Transition edge sensor

value:
/wiki/Bourdon_gauge
mw-redirect
Bourdon gauge

value:
/wiki/Ionization_gauge
mw-redirect
Ionization gauge

value:
/wiki/Permanent_Downhole_Gauge
mw-redirect
Permanent Downhole Gauge

value:
/wiki/Pressure_gauge
mw-redirect
Pressure gauge

value:
/wiki/Flame_detection
mw-redirect
Flame detection

value:
/wiki/Synthetic_aperture_radar
mw-redirect
Synthetic aperture radar

value:
/wiki/Ultrasonic_sensor
mw-redirect
Ultrasonic sensor

value: nowraplinks hlist collapsible collapsed navbox-inner

value: Category:All articles with failed verification

value: Category:Articles with failed verification from July 2016

value: Category:All articles lacking reliable references

value: Category:Articles lacking reliable references from December 2017

value: Category:Articles needing additional references from August 2016

value: Category:All articles needing additional references

value: Category:All articles with vague or ambiguous time

value: Category:Vague or ambiguous time from January 2016

value: Category:Articles containing video clips

value: Discussion about edits from this IP address [ctrl-alt-n]

value: A list of edits made from this IP address [ctrl-alt-y]

value: You are encouraged to create an account and log in; however, it is not mandatory

value: You're encouraged to log in; however, it's not mandatory. [ctrl-alt-o]

value:
/wiki/Smoke_detector
View the content page [ctrl-alt-c]
c

value: Discussion about the content page [ctrl-alt-t]

value: p-namespaces navigation vectorTabs p-namespaces-label

value:
p-variants
navigation
vectorMenu emptyPortlet
p-variants-label

value: Past revisions of this page [ctrl-alt-h]

value: p-views navigation vectorTabs p-views-label

value:
p-cactions
navigation
vectorMenu emptyPortlet
p-cactions-label

value:
mw-wiki-logo
/wiki/Main_Page
Visit the main page

value:
/wiki/Main_Page
Visit the main page [ctrl-alt-z]
z

value: Featured content – the best of Wikipedia

value: Find background information on current events

value:
/wiki/Special:Random
Load a random article [ctrl-alt-x]
x

value: Link to connected data repository item [ctrl-alt-g]

value: Printable version of this page [ctrl-alt-p]

value: portal navigation p-wikibase-otherprojects p-wikibase-otherprojects-label

value: كاشف الدخان – Arabic

value:
interlanguage-link interwiki-ca
display: none;

value:
interlanguage-link interwiki-cs
display: none;

value:
interlanguage-link interwiki-da
display: none;

value:
interlanguage-link interwiki-et
display: none;

value: آشکارساز دود – Persian

value:
interlanguage-link interwiki-fa
display: none;

value: Détecteur et avertisseur autonome de fumée – French

value: 연기 감지기 – Korean

value:
interlanguage-link interwiki-ko
display: none;

value: Impianto di rilevamento incendi – Italian

value:
interlanguage-link interwiki-it
display: none;

value:
interlanguage-link interwiki-nl
display: none;

value: 住宅用火災警報器 – Japanese

value:
interlanguage-link interwiki-no
display: none;

value:
interlanguage-link interwiki-nn
display: none;

value:
interlanguage-link interwiki-pl
display: none;

value:
interlanguage-link interwiki-ro
display: none;

value: Пожарный извещатель – Russian

value:
interlanguage-link interwiki-simple
display: none;

value:
interlanguage-link interwiki-sl
display: none;

value: Детектор дима – Serbian

value:
interlanguage-link interwiki-sr
display: none;

value:
interlanguage-link interwiki-fi
display: none;

value:
interlanguage-link interwiki-sv
display: none;

value: புகையுணரி – Tamil

value:
interlanguage-link interwiki-ta
display: none;

value: స్మోక్ డిటెక్టర్ – Telugu

value:
interlanguage-link interwiki-tr
display: none;

value: Димовий сповіщувач – Ukrainian

value:
interlanguage-link interwiki-uk
display: none;

value:
interlanguage-link interwiki-fiu-vro
display: none;

value:
interlanguage-link interwiki-war
display: none;

value:
interlanguage-link interwiki-zh-yue
display: none;

value: All languages (initial selection from common choices by you and others)

value: /static/images/wikimedia-button-1.5x.png 1.5x, /static/images/wikimedia-button-2x.png 2x

value: /static/images/poweredby_mediawiki_132x47.png 1.5x, /static/images/poweredby_mediawiki_176x62.png 2x

value: mediawiki ltr sitedir-ltr mw-hide-empty-elt ns-0 ns-subject page-Smoke_detector rootpage-Smoke_detector skin-vector action-view